DSL Conductor bar - track are super finished and cross section is maintained to achieve required ampere. The material for track is Aluminum. Conductors shall be accurately aligned to ensure positive electrical contact between the collector and the conductor. Separate conductors shall be provided for each phase. Insulation cover shall be rigid PVC. Range of Ampere available with the material of Aluminum.
ALUMINIUM : 135 Amp. to 315 Amp.
|Type||Bolt Jointed Type Busbar System|
|Insulation Type||PVC (IP35)|
|Ampere Capacity||135 to 315 Amp.|
|Pole Type||1 Pole : Individual. |
3 Pole : RYB
4 Pole. : RYBG
|Jointer Type||4 Bolt Jointed.|
|Standard Length||4.5 Mtr. (4500mm)|
|Mounting Bracket Distance Pitch||1000mm.|
|Busbar Distance Pitch||42mm. (Center)|
|Hanger Clamp||4 Pole : Per Mtr. 1 No.|
3 Pole : Per Mtr. 1 No.
1 Pole : Per Mtr. 4 Nos.
|Anchor Clamp||Per 50 Mtr. 4 Nos.|
|Jointer||Bus bar Jointer is required to Joint 2 bus bars of Standard length of 4.5 Mtr. to make a long travel up to required distance.|
|Joint Cover||Joint cover is used to cover each joint. |
(In Red, Yellow, Blue & Green Colors Available)
|End Cap||End Cap is used to cover DSL ends on either side. That is required one for one Bar/phase.|
|End Power Feed||For DSL system that is powered from ends, "End power feed" is required for Power supply to whole Bus bar system. That is required separately for each phase.|